**ANSI C84.1**is the American National Standard for Electric Power Systems and Equipment – Voltage Ratings (60 Hertz). In 1954, the first version of ANSI C84.1 was basically a combination of the Edison Electric Institute Standard that represents utilities, and the National Electrical Manufacturers Association (NEMA). Currently, the latest version is ANSI C84.1-2011.

The standard establishes the nominal voltage ratings and operating tolerances for 60-Hz electric power systems above 100 volts up to a maximum system voltage of 1200 kV (steady-state voltage levels only). However, in this post, the focus will be on ANSI C84.1 Voltage Ranges. Refer to this article for standard nominal system voltages and voltage classes: ANSI C84.1 - Voltage Ratings.

ANSI C84.1 specifies the steady-state voltage tolerances for an electrical power system. The standard divides voltages into two ranges. Range A is the optimal voltage range. Range B is acceptable, but not optimal.

ANSI C84.1 Voltage Ranges |

**Notes:**

a. The shaded portions of the ranges do not apply to circuits supplying lighting load

b. The shaded portion of the range does not apply to 120 V - 600 V s ystems.

Please take note that transient voltages (i.e. sags and surges) go beyond these limits and are covered by other voltage standards – ITIC and CBEMA Curves.

From the figure above, the following can be deduced:

**For 120 V - 600 V Systems**

__ANSI C84.1 Service Voltage Limits__

Ø Range A minimum voltage is 95% of nominal voltage

Ø Range A maximum voltage is 105% of nominal voltage

Ø Range B minimum voltage is 91.7% of nominal voltage

Ø Range B maximum voltage is 105.8% of nominal voltage

__ANSI C84.1 Utilization Voltage Limits__

Ø Range A minimum voltage is 90% of nominal voltage - refer to Note (a) for limitation

Ø Range A maximum voltage is 104.2% of nominal voltage - refer to Note (b) for limitation

Ø Range B minimum voltage is 86.7% of nominal voltage - refer to Note (a) for limitation

Ø Range B maximum voltage is 105.8% of nominal voltage

**For Systems Greater Than 600 V**

__ANSI C84.1 Service Voltage Limits__

Ø Range A minimum voltage is 97.5% of nominal voltage

Ø Range A maximum voltage is 105% of nominal voltage

Ø Range B minimum voltage is 95% of nominal voltage

Ø Range B maximum voltage is 105.8% of nominal voltage

__ANSI C84.1 Utilization Voltage Limits__

Ø Range A minimum voltage is 90% of nominal voltage

Ø Range A maximum voltage is 105% of nominal voltage

Ø Range B minimum voltage is 86.7% of nominal voltage

Ø Range B maximum voltage is 105.8% of nominal voltage

In addition, the difference between minimum service and minimum utilization voltages is intended to allow for voltage drop in the customer’s wiring. Moreover, this difference is greater for service at more than 600 volts to allow for additional voltage drop in transformations between service voltage and utilization equipment. The National Electrical Code (NEC) allows up to a 5% drop – up to 3% drop in the main feeder and an additional <3% in individual branch circuits.

Therefore, for common nominal system voltages, the recommended range as per ANSI C84.1 for 120 V - 600 V systems will be as indicated below.

ANSI C84.1-2006 Service Voltage Range |

ANSI C84.1-2006 Utilization Voltage Range |

Furthermore, it should be recognized that because of conditions beyond the control of the supplier and/or user, there will be infrequent and limited periods when steady-state voltages exceed Range B limits. Utilization equipment may not operate satisfactorily under these conditions, and protective devices may operate to protect the utilization equipment.

**References:**

ANSI C84.1-2006

Kusko, A. and Thompson, M. (2007).

Pacific Gas and Electric Company. (1999). Voltage Tolerance Boundary

*Power Quality in Electrical Systems*. New York: McGraw-Hill.Pacific Gas and Electric Company. (1999). Voltage Tolerance Boundary

## 2 comments:

ANSI C84.1 - 2011 is published

Hi, I've already updated this post... Thanks for reminding me...

## Post a Comment